before you start Agricultural generator , you should check the fuel tank of oil for usual level, when use it without oil tubing and tapping, keep agricultural water generator cooling system adequate and clean ,keep it from the phenomenon of leakage, fan belt tightness.Check the internal combustion engine and generator parts should be reliable connection, the output circuit wiring insulation is good, is complete and effective in the instrument.
After start Agricultural generator, keep it for 5 minutes on a low speed, valid until its temperature and machine hydraulic wheel are normal, so you can begin to work, the generator should be the same ring in the acc, slip ring and commutator brush contact is good, no beating and sparks.Stay stable running, frequency, voltage rating, then power supply.
Agricultural generator cannot appear in the process of running sound, smell, and the situation of the sharp rise in the water temperature, if any need to stop the machine immediately to check and effective troubleshooting, shall not exceed the late phase generator power factor 0.95 (lag).Changes in the frequency values range shall not exceed 0.5 HZ.
Agricultural generator outage should cut off the power supply branch first before the main switch, gradually reduce the load, and then cut off the generator power supply main switch, the field rheostat answer back to the maximum resistance position, make the voltage drop to the lowest, then cut off excitation switch and neutral point grounding switch, at last stop engine .
Agricultural generator in the process of maintenance of the diesel filter replacement time for every 300 h;Air filter replacement time for every 400 h;Oil filter’s first replacement should be 50 h , after 250 h.Engine oil replacement of 50 h for the first time, then replacement time about every 250 h usually..
WUXI POWER ENGINEERING CO., LTD
Add: No.2721, Jiaoyang Road, Xishan district, Wuxi City, Jiangsu Province, P.R.C.
Contact us: Zhong Young