Seriously do a good job in daily patrol according to the actual usage and operation status of diesel generating set, do necessary maintenance.Use the specified fuel oil, lubricating oil and cooling fluid and change in time;Keep the diesel engine clean, regular check leakage and loose, in order to ensure the normal and reliable work of diesel engine, prolong service life.
1, the filter:
○ air filter:
Every work 50 hours to blowing air compressor mouth clean up one more time.Each running 500 hours or when the red warning device make replacement, replacement of filter press the top button will indicate after him.
○ oil filter:
Period (50 hours or three months) after must be replaced, once every 500 hours or half a year later.Replace filter after switched on for 10 minutes.
Replace the oil filter must be replaced oil at the same time.
○ diesel filter:
After the period (50 hours) must be replaced, once every 500 hours or half a year later.Replace filter after switched on for 10 minutes.
○ cooler filter:
Used for the first time 200 hours or three months must be replaced.After every 500 hours or change once a year.
2, lubricating oil change:
Period (50 hours or three months) must be replaced after, after every 500 hours or replaced once every six months.Oil change at different brands and models of oil shall not be mixed use.Replacing lubricant oil filter must be replaced.
3, cooling fluid replacement:
Used for the first time 200 hours or three months must be replaced.After every 500 hours or change once a year.Pay attention to just stop unit, 15 minutes must not open the tank cover.To prevent water vapor jet cuts.
4, daily routine or check before starting the items:
Checking and removing the oil, water and air leakage phenomenon, wipe the surface of generator set, appearance and diesel engines is kept clean and tidy environment.
(1) keep the cleanness of the whole machine unit.Prevent accumulated water, iron and sundry.
2 check the fuel tank oil level.Ensure the emergency power supply unit.
(3) check the machine oil surface height, whether there are abnormal rise or fall, and find out the reason, when added in a timely manner.
(4) check the water tank.
5] to check the battery voltage, pay attention to add distilled water.
 check each shield is loose and the screw, nut fastening connection parts.
Once enter should pay attention to heat preservation in winter, and injecting antifreeze enough in the tank.
5, unit testing and maintenance operation
○ diesel tank should be clean up once a week, in order to prevent the accumulated water, iron and impurities.
○ for stand-by unit, start a weekly test run operation, examine the dashboard lights, no-load running 5 minutes, each half a month (30%) with moderate load run 15 to 30 minutes.
○ water tank of the belt elasticity check once a week, if there is any wear and should be replaced.
WUXI POWER ENGINEERING CO., LTD
Add: No.2721, Jiaoyang Road, Xishan district, Wuxi City, Jiangsu Province, P.R.C.
Contact us: Zhong Young